In some cases non-compliant points of supply might still be viable, if you would like explore this option please submit a feasibility study.
If you intend to have a new or altered high voltage installation, your electrical contractor will need to submit a HV submission. Please note, this submission doesn’t need to be included with your application, but you will need to submit it before requesting the energisation of your installation.
If you are connected to the high voltage network, at 11kV and 22kV discrete loads up to 4MVA can generally be supplied to one switchboard. Discrete loads 4MVA up to 8MVA must be split evenly across two switchboards (with a maximum of 4MVA per switchboard). For discrete loads above 8MVA, we will assess them on an individual basis.